16-84. M1089 LOWER CONTROL VALVE ASSEMBLY REPLACEMENT/REPAIR (CONT)
Stripper bolt, spring retainers, tube stop,
spring, and linear valve will become very hot
when applying heat to linear valve. Do not
touch these parts with bare hands, or allow
body to come in contact with them. Failure
to comply may result in injury to personnel.
Use care when removing springs. Springs
are under tension and can act as projectiles
when being removed. Failure to comply may
result in injury to personnel.
Do not overheat valve. If linear valve begins
to discolor, remove heat source. Failure to
comply may result in damage to equipment.
Position linear valve in a vise equipped with
vise jaw caps when removing stripper bolt.
Failure to comply may result in injury to
(26) Place linear valve (38) in vise.
(27) Compress spring (39).
(28) Apply heat to linear valve (38) at threads of stripper bolt
(29) Remove stripper bolt (34), two spring retainers (40),
spring (39), and tube stop (41) from linear valve (38).
(30) Perform steps (12) through (29) on remaining solenoid
16-516.2 Change 1